By Tammy from Statham, Ga on August 30, 2013
I have the specifications for my 44 year old Empire propane floor furnace, model #7067. They are: BTU input 70,000, BTU output 49,000, Floor opening 34-5/16 x 30-5/16, Height 27 inches, Diameter of vent 5 inches, Manifold Inlet 1/2 inch. With these, can you tell me what size will fit my need?
By Collin C. - NFI Master Hearth Professional on September 3, 2013
The current model of Empire floor furnace that is a direct replacement for this unit is the Empire 7088 Gas Floor Furnace - Propane - 7088LP
. This model also uses a 5" flue collar and 1/2" supply line. The floor dimensions are exactly the same as your current heater.
By Tammy from GA on August 19, 2013
Looking to replace my 44 year old empire floor furnace model# 7067 BTU 49,000 Rate 70,000LPG. Which one of your models will fit my space?
By Collin C. - NFI Master Hearth Professional on August 20, 2013
Answer:Per the manufacturer, the next version of this unit is the 7088 floor furnace. I was not able to find the original dimensions of the 7067 you have now, but the dimensions of the 7088 are as follows:
Height - 27 inches
Width - 30 Inches
Length - 34 Inches
Register Width - 32 3/4 Inches
Register Length - 36 3/4 Inches
It is possible you will need to reframe the opening for this unit to fit. I apologize that I do not have more information.
By beth from Rhode Island on December 14, 2012
I have a two-story, two room apartment. The kitchen and living room are on the first floor, on a slab. The second room is bedroom and bath and sits over a garage. Each room is smaller than 300 square feet. Is this furnace suitable?
By Tyler M. - Fireplace Specialist on December 14, 2012
By Larry Kannard from Okeene Ok on March 8, 2012
What floor hole size is needed?
By Collin C. - NFI Master Hearth Professional on March 8, 2012
Answer:This unit requires a floor opening of 34 5/16 inches long by 22 5/16 inches wide for proper installation.
You may view additional installation instructions and clearances by downloading the installation manual located on this page.
By Evelyn Harris from Musella, GA 31066 on November 10, 2011
I am trying to find a burner for my propane gas floor furnace, Model 5072, Serial #133677, 45,000 BTU. Do you carry the burners?
By Kevin E. - Fireplace Specialist on November 11, 2011
Answer:Unfortunately, not. We currently only carry the 5088 furnace.
By Collin C. - NFI Master Hearth Professional on November 11, 2011
Answer:I apologize, but we do not have any parts listings for a 5072 furnace and Empire does not recognize this as a model number. Please verify if the unit is spelled Empyre or Empire, as both companies make furnaces, but have completely different product numbers.