By Ray from Mooresville, NC on December 3, 2014
What material is the UL-1618 type 2-36x36 made of?
By eFireplaceStore on December 3, 2014
Answer:The board is constructed of USG brand Micore mineral fiber board, enshrouded in a 30 gauge steel jacket for appearance and strength.
By Brent from Hobbs, NM on August 24, 2014
I own a cast iron stove in a small cabin and it doesn't have a lot of room. Do I need a type 1 or 2 pad?
By eFireplaceStore on August 25, 2014
This model of stove does require a floor protector with an R value, so a Type 2 protector must be used. The Hy-C 36-inch x 52-inch Type 2 UL1618 Black Stove Board
is the smallest factory built board we offer to the 27 by 51 inch floor protector requirements this stove lists. Anything smaller would need to be custom made.
By Joe from Arlington, TX on November 13, 2013
Is there a code for the hearth in front of my fire place? Can I just have my wood floor there? Does something else have to be there and does it have to be a certain size?
By Collin C. - NFI Master Hearth Professional on November 14, 2013
Answer:Per the UL 127 standard for wood burning fireplaces, a hearth extension must be used. For a fireplace with an opening of less than 6 square feet, the hearth protector must extend 8 inches beyond each side of the opening and 16 inches in front of the unit. For a fireplace with an opening of 6 square feet or greater, the hearth protector must extend 12 inches beyond each side of the opening and 20 inches in front of the unit.
By Barbara on November 9, 2012
I have a wood pellet stove and want to put a stove board under it. I see there are two types of boards, Type I and Type II. What is the difference? I see they are only 5/8” thick. Does that offer enough protection if the pad will be on top of a plywood surface?
on November 9, 2012
Answer:The answer to your question all depends on your stove and what the manufacturer of it requires. As far as the types are concerned, Type I boards are ember protectors only. They keep embers from landing on an adjacent combustible surface. Type II boards offer thermal protection in addition to ember protection. These boards have a higher R value.
By Nick on November 9, 2012
I have an antique parlor stove & will required a stove board 6' x 6' square. Do you carry anything in this size & if so, is it UL listed & what is the R rating?
on November 9, 2012
Answer:Unfortunately, the largest square pre-manufactured stove boards that we carry measure 48" x 48". This is because shipment of anything larger than this would have to be done by a specialty freight carrier. Most floor protection that is larger than this would need to be custom made on site, utilizing concrete board and tile or an equivalent noncombustible material.
By Paul on November 9, 2012
I need a floor pad measuring 48 x 60. I don't see that as a specific size. Do you have something close?
on November 9, 2012
Answer:While we do offer 48" x 48" and 36" x 52" boards, we do not carry anything that is larger than these dimensions. This is largely due to the shipping limitations of boards that are any larger than this. Most larger hearth pads must be site built out of concrete board and a ceramic tile or brick of your choosing.
By Loretta on November 9, 2012
We just bought a an antique parlor stove & code requires 18" of space around the stove itself. I'm looking for a stove board that would be 5-1/2' square. Largest size I see you have is 4 x 4.
Can you help me please?
on November 9, 2012
Answer:Unfortunately, you are correct. We do not currently carry a stove board larger than 48" square. Further, we do not customize any of our products. We apologize for the inconvenience.
By Merrilyn from Lacey, WA on September 4, 2013
We would like to use a hearth pad, but the Enviro stove requires venting through the floor of the mobile home. Can we cut a hole in the pad to accommodate the requirements?
By Tyler M. - NFI Certified Specialist on September 4, 2013
Answer:We do not recommend cutting into the stove boards or hearth boards. Doing so with compensate the effectiveness of these boards and cause potential issues with thermal and spark protection.
By Evelyn from Ohio on April 28, 2014
Are either ok to use on the wall behind the woodstove? What is the difference? I need something about 36 x 52".
By Collin C. - NFI Master Hearth Professional on April 29, 2014
By Judy from Madras, OR on November 30, 2012
Can I just order the framework for the hearth pad, so I can put my own tile in it?
By Collin C. - NFI Master Hearth Professional on December 3, 2012
Answer:Unfortunately, no. The metal frames for the hearth pads we sell are cut and welded together on site by the manufacturer. It would be necessary to purchase angled steel to construct your own frame or have a local fabricator cut the steel components to the required size so that they could be screwed or welded together on site.
By Karen Walker from Washington, DC on February 26, 2013
Do you make/sell hearth boards (48 X 48) with an R Factor equal to or greater than 2?
By Tyler M. - Fireplace Specialist on February 26, 2013
By Dan from Cedar City, UT on July 23, 2013
What are the dimensions for the corner pad that is 40 x 49? Is the long side 49" and the short cut side 40"?
By Magan B. on July 23, 2013
Answer:The length is 40" and width is 49".
By Steve from Denver, CO on June 14, 2014
What is the difference between type 2 stove board and 1 UL stove board? I need to protect a wood deck from an outdoor wood portable fire pit.
By eFireplaceStore on June 16, 2014
Answer:Type 1 stove boards offer ember protection only. They are excellent for protection against falling coals or even a log that rolls out of position, but they do not offer any kind of thermal insulation. Type 2 stove boards offer ember and thermal protection. They will utilize a layer of built in material, usually mineral board, which helps to shield the area below from excessive heat. If the fire pit is low to the ground and could potentially damage a combustible surface beneath it, the Type 2 board would be the product to use.